With all of the push for top-of-rack switches, is this the end of copper structured cabling?
Absolutely not. Most of the top-of-rack switches are now available with 10GBASE-T ports. This allows for longer cables that are directly meant for copper structured cabling. The benefit here is that by centralizing the switches into distribution areas or zones, you open up the switch ports to a greater number of servers and end devices due to the cable.
I think it is important to note that a well-planned, well designed cable plant never causes cooling problems, but a bunch of point-to-point connections certainly can. If you look at the amount of savings you can have with switch ports when they are deployed in zones rather than top of rack switches, it is significant. Generally what you end up saving, pays for the copper structured cabling. I work with end users on design often, and zones save significant amounts of money (some upwards of 5 million) for larger data centers. It is important to understand how the switches work and what the options are before you believe marketing material which may not be the best design for your enterprise.
Do you have a question for our experts?
Submit your question directly to our editors at email@example.com.
What standards specify flame retardant cable jackets for Europe?
How does channel length affect patch cord length?
How to set QoS for users connected to ever-changing switch ports
Dig Deeper on Data Center Networking
Related Q&A from Carrie Higbie Goetz
Proper SBC configuration requires partnering with providers and security teams to examine circuits and potential traffic. Learn the best practices ... Continue Reading
Organizations need SIP services to connect and disconnect call sessions. Now some SIP services are offered through APIs, which expand the use cases ... Continue Reading
A few factors can indicate it's time to replace a business phone system. Learn when it may be time to switch and how to decide on a course of action. Continue Reading