There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Infrastructure
Related Q&A from Carrie Higbie Goetz
Our expert explains the UC monitoring tools you need and the potential network problems you may discover in your UC and collaboration environments. Continue Reading
When your SIP service isn't connecting properly, process of elimination will help you determine if the issue lies in your configuration or elsewhere ... Continue Reading
The requirements for cloud-based unified communications certifications vary by industry and network environment. UC expert Carrie Higbie Goetz ... Continue Reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.