There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie Goetz
Preparing for a UCaaS deployment means having the right WAN circuit configuration, with enough bandwidth to support all of your data and prioritize ... Continue Reading
What an organization moves to the cloud will influence UC devices and endpoints. Networking expert Carrie Higbie Goetz explains the factors that ... Continue Reading
As SD-WAN grows in popularity, enterprise SBCs still have their place on the network. Learn how the two technologies can work together to support and... Continue Reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.