What are the industry best practices for cabling high-density production server cabinets without patch panels?...
By submitting your email address, you agree to receive emails regarding relevant topic offers from TechTarget and its partners. You can withdraw your consent at any time. Contact TechTarget at 275 Grove Street, Newton, MA.
My boss wants to eliminate the hard costs of patch panels. My networking environment is edge to core. The cabinet density is 40 x 1 U servers per cabinet.
This is generally not recommended. There are several reasons including the fact that what you end up with is a lot of long patch cables. The fixed horizontal lengths should be fixed. It is far easier for troubleshooting and in fact is likely going to be better for performance. Cords become tangled, unsupported and, in general, very difficult to manage. There may also be performance issues depending on the lengths of the cords and applications. However, there are some companies that do this anyway, despite the risks. You will need to find a mechanism either underfloor or overhead to go from the switch to the server ports. While you may eliminate the patch panels, you will still have to figure out a way to properly support the cords and maintain appropriate bend radii.
Some companies have moved to putting patch panels under the floor or overhead in the cable trays. This option provides the best of both worlds as it eliminates the density in the cabinet. Be sure to check with your cabinet manufacturer to determine the proper fill ratios for their cabinet openings.
Related Q&A from Carrie Higbie
Networking expert Carrie Higbie explains how a VoIP gateway and an IP PBX perform different functions when transmitting voice data.continue reading
UC expert Carrie Higbie explains the purpose of Port 9875 and why a network manager would need to direct traffic to this port in a VoIP setup.continue reading
How can you make sure your UC infrastructure can keep up with mobile device software and hardware updates? Expert Carrie Higbie explains how to ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.