What are the differences between PVC, riser and plenum rated cables?
By submitting your email address, you agree to receive emails regarding relevant topic offers from TechTarget and its partners. You can withdraw your consent at any time. Contact TechTarget at 275 Grove Street, Newton, MA.
PVC, or PolyVinylChloride, refers to the coating of the cable jacket. If you have riser or plenum rated cables, they are slower to burn and produce less smoke than PVC and are rated to be installed in plenum areas (any area with return air). Riser cable is the minimum required cable for a riser application (floor to floor). There is also a newer kind of cable called limited combustible cable. In some jurisdictions the AHJ (authority having jurisdiction) supports the sprinkler standard which states that if you don't have LCC (limited combustible cable) then you have to install sprinklers under the raised floor and in the ceiling plenums. If you use PVC cable, you MUST install it in conduit if it is in plenum areas. There are three standards governing what type of cable you must use (I am assuming you are in the US… if not, the standards are a bit different. If you aren't in the US, let me know where you are and I will help you with the standards). The standards in the US include National Electrical Code, (NFPA 70), NFPA 90A (Standard for Air Conditioning and Ventilation equipment) and NFPA 13, which governs the use of sprinklers. In the last two, sprinklers are not required if you use LCC cable. In 90A, combustible cables such as CMP, CMR are allowed as an exception but LCC is required. The problem was that for years, we did not have LCC cable. Whatever you chose, you will want to talk to your inspector to determine if you will need additional sprinklers if you use plenum rated cable rather than LCC or if you will need conduit.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie
As the number of connected devices and UC applications grows in the enterprise, IT must take steps to improve the network, such as adding access ...continue reading
When migrating to VoIP training must extend beyond the IT department. End users will need training on features such as voicemail and conference calls...continue reading
While software-defined networking is still in its early stages, there are some SDN use cases for UC that can make managing applications and services ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.