There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology...
By submitting your email address, you agree to receive emails regarding relevant topic offers from TechTarget and its partners. You can withdraw your consent at any time. Contact TechTarget at 275 Grove Street, Newton, MA.
areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie
As the number of connected devices and UC applications grows in the enterprise, IT must take steps to improve the network, such as adding access ...continue reading
When migrating to VoIP training must extend beyond the IT department. End users will need training on features such as voicemail and conference calls...continue reading
While software-defined networking is still in its early stages, there are some SDN use cases for UC that can make managing applications and services ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.