There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology...
By submitting your email address, you agree to receive emails regarding relevant topic offers from TechTarget and its partners. You can withdraw your consent at any time. Contact TechTarget at 275 Grove Street, Newton, MA.
areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie Goetz
Organizations must ensure their networks can support employees' current and future video collaboration needs. Learn how to evaluate your network's ...continue reading
A UC cloud-based architecture has similar network needs as on-premises systems. Networking expert Carrie Higbie Goetz explains why SBCs are necessary...continue reading
Network monitoring software helps organizations manage the demanding real-time traffic of UC apps. Networking expert Carrie Higbie explains how to ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.