There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology...
areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie Goetz
WebRTC services can supplement your UC architecture and real-time collaboration strategy. Discover the benefits of deploying WebRTC to simplify ...continue reading
Learn about the various bandwidth services organizations can purchase to support their business apps and how they can effectively manage their ...continue reading
Organizations must ensure their networks can support employees' current and future video collaboration needs. Learn how to evaluate your network's ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.