There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology...
areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie, Data Center Networking Expert
With a growing number of online resources, is the Magic Quadrant still the No. 1 source of vendor information?continue reading
To view networking infrastructure and project management expert Carrie Higbie's latest advice, see her Public Profile on the IT Knowledge Exchange.continue reading
Find out the industry standards for twisted pair cable length in this response from network infrastructure expert Carrie Higbie.continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.