There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology...
By submitting your personal information, you agree that TechTarget and its partners may contact you regarding relevant content, products and special offers.
areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie Goetz
Preparing a request-for-proposal document for a potential UC cloud service requires several elements. Learn how to craft a thorough RFP to meet your ...continue reading
Security is a priority when moving communications to the cloud. Organizations must do their due diligence when evaluating cloud providers' UC ...continue reading
Video quality can suffer if the network can't meet its high bandwidth needs. Networking expert Carrie Higbie Goetz explains how SD-WAN supports video...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.