There are things that can interfere, in particular in a hospital, particularly around the teleradioloy or radiology...
By submitting your personal information, you agree that TechTarget and its partners may contact you regarding relevant content, products and special offers.
areas. Many hospitals opt for shielded cabling systems (still generally Category 6), however some still use the unshielded variety. But pay particular attention to where the cable paths are run. This may also be true around dialysis machines and other machines that require higher voltages. No cabling system will work properly or support your applications if it was not installed properly.
As for your plenum question, that depends on whether the return vents are ducted or not. If they are not (which is usually the case) then yes, the cable must be plenum rated. There is also language in the new national electrical code that states that it must be limited combustible cable or those areas must be have sprinklers. Your local inspector can provide you with guidance in this area.
Dig Deeper on Network Hardware
Related Q&A from Carrie Higbie Goetz
The growing use of collaboration apps is putting pressure on the business mobile network. Learn how to support collaboration on both mobile and Wi-Fi...continue reading
Learn how to prepare your organization for a SIP deployment through a clearly defined evaluation of your organization's network requirements and ...continue reading
Virtualizing enterprise session border controllers can help reduce business expenses. Networking expert Carrie Higbie Goetz explains how to deploy ...continue reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.